THE FIREDETEC® DIFFERENCE
Rotarex FireDETEC® systems use a proprietary continuous linear sensor tube that reliably detects and actuates release of the extinguishing agent using pneumatic technology. It is more flexible, space efficient and cost effective versus alternative mechanical or electronic systems.
1. Quick & Easy installation directly inside the ATM housing compartments:
The flexible sensor tubing is easily installed directly above and around
the ATM enclosure - closer to where a fire could start.
When in service, the tubing is pressurized with dry nitrogen to 16 bar.
The dynamics of pressurization make the tubing more reactive to heat.
2. Early fire detection:
If a fire occurs, the heat of the fire causes the pressurized sensor tube to burst at the hottest spot (approx. 110°C)
3. Instant suppression:
The sudden tube depressurization actuates the special pressure differential valve and instantly floods the entire ATM interior compartment with extinguishing agent. The fire is quickly suppressed just moments after it began... minimizing damage and downtime.
CHOOSE FROM 3 SUPPRESSION AGENTS : A MATTER OF PREFERENCE
FIRE PROTECTION FLUID